You’ve heard a lot of talk about the deployment of the Smart Grid. Most of the initial smart grid deployments are focused on the de-ployment of smart meters that enable utilities to gather usage information in near real time — or what they call Automated Meter Infrastructure (AMI).
The application of energy recovery units allows for the ability to do total heat recovery and recover both sensible and latent heat from an exhaust air stream, using that heat to pre-condition outdoor air required for building ventilation.
In a campus environment over time, it’s not hard to lose control of the controls. When you tackle the situation for the long-term good, take time to create a master plan. Get a few tips on that here, and then move on to issues such as protocols, access, graphics, and trending. Your best possible BAS is not out of reach.
Both new and existing building projects should have lighting control provided, either as part of a standalone system or, ideally, integrated as part of the BAS. But we often find that there are many reasons automated lighting control is not provided, ranging from simple economics to frustration with the programming and support of these systems.
Leaning on experience and data from various K-12 cities and projects, the author pursues some less conventional design approaches. They may revolve around radiant heating and/or cooling, but depending on school size and other factors, the smart use of heat recovery, DOAS, and improved central plants could also put a project on the HVAC honor roll.