As the saying goes, the journey of a thousand miles begins with one step. On a data center project, some tailored software can often point things in the right direction. Novices and grizzled veterans alike would be wise to peruse some of these options for maximizing their new construction and retrofit results.
What is the difference between a typical BAS scenario and one that involves building analytics? And why did one library start to see its utility costs and trouble calls start to spiral upward? As you might imagine, the answers to these questions are related …
Since the early ’80s, building automation technology (BAS) have played an integral role in engineers’ ability to aid facility owners and operators in achieving operational efficiency, dependable comfort, and lower energy costs. However, despite significant capital investments, often times the full potential of these systems is not realized, resulting in less than optimal building performance.
In theory, a BAS provides all of the hardware and software required to analyze and operate all functions within a building. In reality, though, what most of these systems do best is control the HVAC system.
Many engineers tend to avoid or delegate the nitty gritty of a ground source heat pump system, from soil moisture effects to building system (im) balance. It's time for designers to get in the loop. Learn more about Grounded In Reality in the December issue. Other topics in the December issue include health care HVAC, Boilders, check out the Back2Basics, and more.