Retrofitting more than a half-million square feet of heavily used space for better life safety coverage is never simple. Peculiarities of building design and existing materials only made the task tougher for this project team as they sought to integrate NFPA and GSA requirements into a successful and safe solution.
This month, our life safety coverage arrives from the commissioning side. From design phase to tips on navigating a seemingly untenable number of observations, and on to post-testing tasks, here’s one consultant’s solid reference to keep you and your client from getting unnecessarily alarmed.
Incorporating a plenum can have its design advantages, but corridors serving adjoining areas of health care occupancies are prohibited from being used for a portion of an air supply, air return, or exhaust air plenum. This article and its illustrations can strengthen your grasp of the related NFPA code details and exceptions so you can design and ventilate properly for this special population.
A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.