How often does an existing closed loop hot water heating or chilled water cooling system get reused as part of a building renovation project, and/or used to expand the area served by the system coverage to provide additional heating or air conditioning?
This past May I wrote in the Back2Basics column about the design intent of a small city school system that chose to invest in an annual contract for a temporary air-cooled chiller for special events and emergency crisis shelter center.
Probably a year before 9/11, I was asked my thoughts along the lines of, “What else should we commission beyond the standard building systems?” My client was the project engineer at the Department of Defense in the Pentagon. I suggested “commission project record drawings.” I guess you could say I made up the task of commissioning record drawings, but I got my point across.
Spot exhaust is a unique design engineering challenge. The 2015 ASHRAE Handbook – HVAC Applicationscovers a broad spectrum of applications in just about all the comfort applications (chapters 1 through 13) and industrial applications (chapters 14 through 33) with personal safety an integral part of chapter 32. But spot return air doesn’t get much press in ASHRAE.
When I got started in the HVAC business half a century ago, I was very fortunate to work for a small firm where I learned a lot about design engineering from some really knowledgeable and practical HVAC engineers. The business we were in was designing HVAC for hospitals, colleges, universities, research facilities, and museums. All of these facilities required very sophisticated central air systems, heating systems, and chilled water systems.
From a missing pipe hanger three floors down to steam traps past their prime, these stories show how steam system problems can originate inside the boiler room or far beyond it. Read more in February issue.