You’ve heard a lot of talk about the deployment of the Smart Grid. Most of the initial smart grid deployments are focused on the de-ployment of smart meters that enable utilities to gather usage information in near real time — or what they call Automated Meter Infrastructure (AMI).
The application of energy recovery units allows for the ability to do total heat recovery and recover both sensible and latent heat from an exhaust air stream, using that heat to pre-condition outdoor air required for building ventilation.
Both new and existing building projects should have lighting control provided, either as part of a standalone system or, ideally, integrated as part of the BAS. But we often find that there are many reasons automated lighting control is not provided, ranging from simple economics to frustration with the programming and support of these systems.
A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.