An air handling unit that hasn’t worked since, well, ever. Chillers that have to work more often as a result — and an extra chiller just to attack the affected zone. These were the obvious symptoms, but what was the cause?
Retrieving every last bit of performance from the system while stopping short of the surge line is no small feat. Dig into sizing, tower selection, chilled water loads and stability, and condenser water management to leave no efficiency stone unturned. Read more in April issue