A. O. Smith launch of its Commercial Heat Pump Water Heater (CHP-120) for light commercial applications such as restaurants, schools, retail buildings or any facility which would traditionally use a standard commercial electric water heater.
The high-profile equipment involves an efficient, resilient trigeneration plant to provide heating, cooling, and power service. However, UConn’s most critical asset may be its forward-thinking, campus-wide energy strategy.
While CHP is good, CCHP can be even better for your facility and its locale. The author surveys the potential benefits, building code input, and electrical considerations. After a couple of case studies, she then reviews considerable engineering re-sources the DOE provides for those contemplating a forward-looking but proven design.
More specifically, has natural gas been overlooked? Let’s take a look at some previous habits and code language, current needs, and the advantages that a CHP system can provide for those exceedingly regulated of all environments: hospitals.
It might seem like an odd objective, but the potential efficiency gains are real. And from heat recovery chillers to modified humidification targets so are the opportunities to replace steam production with hot water generation and to manage remaining steam needs more intelligently.
The production of thermal power is critically important in carrying out the mission of health care facilities where it is used for space heating, humidification, domestic water heating, and for processes in dietary, laundry, and sterilization departments.
A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.
It’s not necessarily a plug-and-play situation, but these chillers can play key roles and deliver meaningful savings in several scenarios. Waste heat, CCHP, standalone, and even renewable solar as part of the refrigeration cycle can all provide the setting for absorption success.