Trends don’t always follow the expected path (or timeline), but the basics remain the basics and increased cabinet density remains inevitable. Let’s revisit the progress of liquid in data center strategy and the tenets of a future-proof(ish) hybrid design for today.
While CHP is good, CCHP can be even better for your facility and its locale. The author surveys the potential benefits, building code input, and electrical considerations. After a couple of case studies, she then reviews considerable engineering re-sources the DOE provides for those contemplating a forward-looking but proven design.
As we continue to look for weapons to fight hospital-acquired infections (HAI), what does the standard for health care facility ventilation already contain in the way of health metrics? How would a study look if it focused on the one metric that drives so many other decisions in health care? Let’s explore.
As the saying goes, the journey of a thousand miles begins with one step. On a data center project, some tailored software can often point things in the right direction. Novices and grizzled veterans alike would be wise to peruse some of these options for maximizing their new construction and retrofit results.
Hospitals in the U.S., already facing daunting challenges from evolving health care reimbursement models, now have another item on their to-do list: prepare for increased health care demands and weather disasters caused by climate change.
More specifically, has natural gas been overlooked? Let’s take a look at some previous habits and code language, current needs, and the advantages that a CHP system can provide for those exceedingly regulated of all environments: hospitals.
Emergency generators are required in many applications where facility operations are to continue to perform even upon a failure of the electric grid. The best resources for quantifying the emergency generation classifications, capacities, installation, maintenance, and operational testing requirements are the building codes and federal regulations.
Retrieving every last bit of performance from the system while stopping short of the surge line is no small feat. Dig into sizing, tower selection, chilled water loads and stability, and condenser water management to leave no efficiency stone unturned. Read more in April issue