As the saying goes, the journey of a thousand miles begins with one step. On a data center project, some tailored software can often point things in the right direction. Novices and grizzled veterans alike would be wise to peruse some of these options for maximizing their new construction and retrofit results.
What is the difference between a typical BAS scenario and one that involves building analytics? And why did one library start to see its utility costs and trouble calls start to spiral upward? As you might imagine, the answers to these questions are related …
Since the early ’80s, building automation technology (BAS) have played an integral role in engineers’ ability to aid facility owners and operators in achieving operational efficiency, dependable comfort, and lower energy costs. However, despite significant capital investments, often times the full potential of these systems is not realized, resulting in less than optimal building performance.
In theory, a BAS provides all of the hardware and software required to analyze and operate all functions within a building. In reality, though, what most of these systems do best is control the HVAC system.
Retrieving every last bit of performance from the system while stopping short of the surge line is no small feat. Dig into sizing, tower selection, chilled water loads and stability, and condenser water management to leave no efficiency stone unturned. Read more in April issue