An air handling unit that hasn’t worked since, well, ever. Chillers that have to work more often as a result — and an extra chiller just to attack the affected zone. These were the obvious symptoms, but what was the cause?
This is the second in a series of columns in which I am demonstrating examples of systems performance information that can be gleaned from trend log analysis. In these columns, I introduce a system or sub-system, show a trend graph, and then leave it up to the reader to discover the operational “issue” illustrated in the graph. The answer will be given at the start of the subsequent month’s column.
A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.