After 40 years and other engineering studies, a large university building still suffered from humidity problems. Our intrepid author dug into the data and the dark corners of the building in pursuit of the culprit — or culprits?
An air handling unit that hasn’t worked since, well, ever. Chillers that have to work more often as a result — and an extra chiller just to attack the affected zone. These were the obvious symptoms, but what was the cause?
From a missing pipe hanger three floors down to steam traps past their prime, these stories show how steam system problems can originate inside the boiler room or far beyond it. Read more in February issue.