After 40 years and other engineering studies, a large university building still suffered from humidity problems. Our intrepid author dug into the data and the dark corners of the building in pursuit of the culprit — or culprits?
An air handling unit that hasn’t worked since, well, ever. Chillers that have to work more often as a result — and an extra chiller just to attack the affected zone. These were the obvious symptoms, but what was the cause?
Boiler Maintenance & Lifecycle Costs; Proper upkeep can seem like a high bar, but it's nothing compared to a drain on the budget, an avoidable full replacement, or an on-site incident, read more in January issue.