A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.
It’s not necessarily a plug-and-play situation, but these chillers can play key roles and deliver meaningful savings in several scenarios. Waste heat, CCHP, standalone, and even renewable solar as part of the refrigeration cycle can all provide the setting for absorption success.
While mechanical energy codes may lag relative to the efficiency targets of some other codes , the expansion of VRF into a wider range of equipment makes it easier than ever to exceed expectations. Perhaps more importantly, its incorporation into heat pumps, dehu-midifiers, compressors, and more represents more flexibility in delivering an effective retrofit without a total system overhaul.
Leaning on experience and data from various K-12 cities and projects, the author pursues some less conventional design approaches. They may revolve around radiant heating and/or cooling, but depending on school size and other factors, the smart use of heat recovery, DOAS, and improved central plants could also put a project on the HVAC honor roll.