UFAD and displacement ventilation systems require accurate estimates to meet relative humidity requirements and ensure efficient operations. Take a look at a few design options, and contemplate the reader challenge at the end.
Since their introduction in Europe in the 1950s, and their domestic rise in specification during the 1990s, UFAD and displacement ventilation systems promise significant energy savings as a direct result of a higher supply air temperature that yields an increase in the use of economizer or free cooling hours.
Why was one floor’s laboratory ventilation failing to keep up, when it was even the closest floor to the rooftop fans? Some system sleuthing led two engineers to a fitting conclusion. Read more stories in May Issue 2017.