UFAD and displacement ventilation systems require accurate estimates to meet relative humidity requirements and ensure efficient operations. Take a look at a few design options, and contemplate the reader challenge at the end.
Since their introduction in Europe in the 1950s, and their domestic rise in specification during the 1990s, UFAD and displacement ventilation systems promise significant energy savings as a direct result of a higher supply air temperature that yields an increase in the use of economizer or free cooling hours.
From a missing pipe hanger three floors down to steam traps past their prime, these stories show how steam system problems can originate inside the boiler room or far beyond it. Read more in February issue.