Read about various examples — from a 40,000-sq-ft raised-floor environment to a 5,000-sq-ft facility within a facility — to get a good view of the battlefield and make your next campaign against heat and inefficiency a little smarter.
The range of HVAC design options associated with the various types of data centers has expanded and evolved over the past 30 years in order to keep pace with the wide array of server transformations and deployment strategies.
A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.