Generally, when we think about BAS, it is in the context of large commercial buildings, those well over 25,000 sq ft. According to the latest government data though (from the 2012 Commercial Building Energy Consumption Survey), 88% of all commercial buildings are 25,000 sq ft or less.
Beginning with whether or not a drive is even needed, the article moves on to help you clear hurdles involved with motor compatibility, existing starters, drive reliability, controls integration, and more.
Few areas can be as tough to condition as pools and ice rinks. Indoor pools, or natatoriums, need to be able to maintain a space temperature warmer than the water temperature and space humidity between 50% to 60%.
Many engineers tend to avoid or delegate the nitty gritty of a ground source heat pump system, from soil moisture effects to building system (im) balance. It's time for designers to get in the loop. Learn more about Grounded In Reality in the December issue. Other topics in the December issue include health care HVAC, Boilders, check out the Back2Basics, and more.