Generally, when we think about BAS, it is in the context of large commercial buildings, those well over 25,000 sq ft. According to the latest government data though (from the 2012 Commercial Building Energy Consumption Survey), 88% of all commercial buildings are 25,000 sq ft or less.
Beginning with whether or not a drive is even needed, the article moves on to help you clear hurdles involved with motor compatibility, existing starters, drive reliability, controls integration, and more.
Few areas can be as tough to condition as pools and ice rinks. Indoor pools, or natatoriums, need to be able to maintain a space temperature warmer than the water temperature and space humidity between 50% to 60%.
Retrieving every last bit of performance from the system while stopping short of the surge line is no small feat. Dig into sizing, tower selection, chilled water loads and stability, and condenser water management to leave no efficiency stone unturned. Read more in April issue