Parallel or opposing blades for the best mix of air in VAV systems? What about deploying filtration only when you really need it, thereby avoiding unnecessary pressure drop? Include some ideas about economizer control and another vote for CO2 sensors and demand-controlled ventilation, and you've got some worthwhile - if not always traditional - answers for airside controls blowin' in the wind.
A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.