What determines chiller plant loading? Do connected plants need to use similar pumping schemes? Is it better to run one chiller in multiple plants or multiple chillers in one plant? Draw on the author’s experience for answers. Then learn how to handle the hydraulics of interconnection and enjoy the byproducts of a well-integrated system.
Retrieving every last bit of performance from the system while stopping short of the surge line is no small feat. Dig into sizing, tower selection, chilled water loads and stability, and condenser water management to leave no efficiency stone unturned. Read more in April issue