Where do health care facilities looking to up their sustainability profile start? Here, we shine
a light on expected sites and some lesser-known resources. Archived video from conferences,
toolkits for benchmarking, assessing a facility for CHP, general design guides, and even primers for executives looking to get the ball rolling … ideas and tips for good design and operations run a lot deeper than LEED®.
A solar array contributed to putting this insurance headquarters in hot water — in a good way. See how those systems teamed with chiller plant improvements to maintain occupant and computer room productivity.
“Not enough airflow.”
These were just a few of the countless complaints that facilities managers of the Basic Medical Science Building at the University of New Mexico were receiving on a regular basis.
Whether at work or in our personal lives, we all try to be smart shoppers. We’ll go that extra mile to save a few percent on upfront purchase costs but every so often miss the big picture by not taking total cost of ownership (TCO) into account.
Last September, on what would normally have been a mild autumn day, Southern California was blasted by a record-breaking heat wave with temperatures spiraling upwards to 116°F in the Los Angeles basin. The heat was far above the normal highs, which would typically be in the mid-70s.
Located in this city’s famous Loop commercial center, the 600-foot-tall Chicago Board of Trade Building (CBOT) houses the world’s oldest futures and options exchange. Until recently, the building also housed a pair of aging built-up systems that were beginning to worry management.
A lot has happened since the author’s 2008
article. It’s prime time to revisit expectations for BAS and chiller
optimization controls, and then have a look at several of today’s options for
anyone managing chilled water flow to wring the last drop of efficiency out of