As one of the largest commercial real estate firms in the southeastern United States, Childress Klein oversees and services nearly 40 million sq ft of office, industrial, retail and residential properties.
Trends don’t always follow the expected path (or timeline), but the basics remain the basics and increased cabinet density remains inevitable. Let’s revisit the progress of liquid in data center strategy and the tenets of a future-proof(ish) hybrid design for today.
Thanks to a recent remodeling, patrons seated indoors experience the ambience of dining outdoors at O’Toole’s Irish American Grill & Bar. However, there are no mosquitoes, flies, or vehicle emission odors, and the temperature is always a comfortable 74°F.
Why do ground loops in moist soils sometimes perform better than expected? What ground loop design tactics can address building system imbalance? Engineers need to take more responsibility for their full GSHP designs, and these questions are a good place to start.
With a little guidance on ground-source heat pump design temperatures and a few rules of thumb for ground loop flow rates, most engineers are pretty comfortable designing the building side of a ground-source heat pump (GSHP) system.
While CHP is good, CCHP can be even better for your facility and its locale. The author surveys the potential benefits, building code input, and electrical considerations. After a couple of case studies, she then reviews considerable engineering re-sources the DOE provides for those contemplating a forward-looking but proven design.
The larger or more complex a cooling plant becomes, the more challenges to its ef-ficiency it will face. When applied wisely, modern controls and equipment can rise to meet those challenges. Read up on active balancing, pump dynamic differential setpoint control, and more responsive tactics for when the worst thing you can do is just go with the flow.
Boiler Maintenance & Lifecycle Costs; Proper upkeep can seem like a high bar, but it's nothing compared to a drain on the budget, an avoidable full replacement, or an on-site incident, read more in January issue.