Consider these factors when sizing up a potential upgrade. In addition, pick up a few easy tips for maintenance in the meantime. You can’t necessarily buy time, but you can get in front of a worst-case breakdown scenario.
Sometimes it does pay to sweat the small stuff. Data availability might vary depending simply on where you’re accessing it. Not only selection but placement of your sensors and transmitters can influence their effectiveness and response time. Bearing down on such details on the BMS side can yield long-term results for your cooling goals.
Clarify the difference between pressure dependent and pressure independent systems, and then make a deep dive into this TAB process. There’s a lot of science involved, but in the end, steering and tweaking the process may seem more like an art.
Hotels and other high-rise buildings can easily develop indoor humidity issues if they don’t deal properly with the outside air component of their ventilation design. Reclaiming waste heat in a way that suits the circumstances can be a pivotal step toward correcting or avoiding such problems. With a Chicago condo as one example, learn to work through assorted benefits and caveats to reach the right fix.
Many engineers tend to avoid or delegate the nitty gritty of a ground source heat pump system, from soil moisture effects to building system (im) balance. It's time for designers to get in the loop. Learn more about Grounded In Reality in the December issue. Other topics in the December issue include health care HVAC, Boilders, check out the Back2Basics, and more.