In which CFD modeling lets us compare two possible design configurations for ventilation in a hospital patient room, yielding some similarities and perhaps surprising differences in what each configuration means for pathogen control and occupant comfort.
We’ve made some progress, but the fight against hospital-acquired infection (HAI) remains long and uphill. Here, we look at various risks and strategies, putting some thoughts on a wise approach to humidification in the context of the HAI battle.
The Museum of the Bible’s project team was already up against the extremes of Washington weather and the high demands of IAQ for artifact preservation. A system that harnessed adequate cooling, heating, humidification, and ventilation capabilities would still have one more hurdle: a physical footprint of hardly Biblical proportion. Get a first look at this testament to design acumen and true collaboration.
A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.