An advance investigation into the needs and preferences of the medical team proved in valuable for a Virginia hospital retrofit. The range of desired OR conditions was demanding, but for good reason. The designers, armed with this info, applied experience and mechanical muscle to provide the environmental flexibility to operate from one patient to the next.
Carilion Clinic is a not-for-profit health care organization based in Roanoke, VA. In line with their mission to improve the health of the communities they serve, and with the intent of becoming a teaching facility, Carilion Clinic set upon upgrading their operating rooms and related existing HVAC systems at the Carilion New River Valley Medical Center in Christiansburg, VA.
While CHP is good, CCHP can be even better for your facility and its locale. The author surveys the potential benefits, building code input, and electrical considerations. After a couple of case studies, she then reviews considerable engineering re-sources the DOE provides for those contemplating a forward-looking but proven design.
As we continue to look for weapons to fight hospital-acquired infections (HAI), what does the standard for health care facility ventilation already contain in the way of health metrics? How would a study look if it focused on the one metric that drives so many other decisions in health care? Let’s explore.
The larger or more complex a cooling plant becomes, the more challenges to its ef-ficiency it will face. When applied wisely, modern controls and equipment can rise to meet those challenges. Read up on active balancing, pump dynamic differential setpoint control, and more responsive tactics for when the worst thing you can do is just go with the flow.
Consider these factors when sizing up a potential upgrade. In addition, pick up a few easy tips for maintenance in the meantime. You can’t necessarily buy time, but you can get in front of a worst-case breakdown scenario.
Sometimes it does pay to sweat the small stuff. Data availability might vary depending simply on where you’re accessing it. Not only selection but placement of your sensors and transmitters can influence their effectiveness and response time. Bearing down on such details on the BMS side can yield long-term results for your cooling goals.
Clarify the difference between pressure dependent and pressure independent systems, and then make a deep dive into this TAB process. There’s a lot of science involved, but in the end, steering and tweaking the process may seem more like an art.
Hotels and other high-rise buildings can easily develop indoor humidity issues if they don’t deal properly with the outside air component of their ventilation design. Reclaiming waste heat in a way that suits the circumstances can be a pivotal step toward correcting or avoiding such problems. With a Chicago condo as one example, learn to work through assorted benefits and caveats to reach the right fix.
In which the author explores the specific strengths and attributes of various boiler types, along with pumping options and other system factors. The goal: To help you intelligently align your project’s equipment choices with its particular load, meeting expectations while avoiding Delta T headaches.