It might seem like an odd objective, but the potential efficiency gains are real. And from heat recovery chillers to modified humidification targets so are the opportunities to replace steam production with hot water generation and to manage remaining steam needs more intelligently.
The production of thermal power is critically important in carrying out the mission of health care facilities where it is used for space heating, humidification, domestic water heating, and for processes in dietary, laundry, and sterilization departments. The age of the hospital, the programs offered, and the regional climate will all affect the demand for thermal power.
Spot exhaust is a unique design engineering challenge. The 2015 ASHRAE Handbook – HVAC Applicationscovers a broad spectrum of applications in just about all the comfort applications (chapters 1 through 13) and industrial applications (chapters 14 through 33) with personal safety an integral part of chapter 32. But spot return air doesn’t get much press in ASHRAE.
Continuing last month’s topic of commissioning action lists (a.k.a. master issues logs, a.k.a. corrective action lists), I would like to focus on the items in those documents that deal with construction phase or acceptance testing “deficiencies.”
Uniform Solar Energy and Hydronics Code (USEHC) contains some requirements that may be inappropriate given certain conditions, climates, or simple designer discretion. That’s not a problem … unless your locality or state adopts USECH language as binding. Dig into the problem and note a timely opportunity to avoid having these issues set in stone for another few years.
As early as 3000 BC, civilizations began to create codes for public order and safety. The Code of Hammurabi, the old “eye for an eye” law many are familiar with, also included laws for safe building construction.
Once we distinguish voltage unbalance from voltage variation, the need to tackle the issue intelligently becomes even more clear. Learn about common causes and effects, testing for unbalanced voltages and single-phasing, and ways to correct the problem if it does manage to arise.
So many areas where a little forethought and awareness can avoid larger problems — sizing, velocity, piping and connections, double trapping, condensate return, proper pressure, blowdown tanks, and more. Read on for some good habits and why they’re worth having.
When designing or replacing a low pressure steam boiler, throw out everything you know about hydronic boilers. A steam system is closer in operation to an air conditioning unit than it is to a hydronic boiler. If you design a steam system using hydronic design methods, it will not operate properly.
Leaning on experience and data from various K-12 cities and projects, the authors pursue some less conventional design approaches. They may revolve around radiant heating and/or cooling, but depending on school size and other factors, the smart use of heat recovery, DOAS, and improved central plants could also put a project on the HVAC honor roll.
From a missing pipe hanger three floors down to steam traps past their prime, these stories show how steam system problems can originate inside the boiler room or far beyond it. Read more in February issue.