After reviewing basic design options, the next steps for potential geothermal designers are to challenge the common concerns and myths, study how different choices have different cost impacts, and be aware of the ways a good design can yield bad performance if the installation isn’t done well. Add the habit of turning a retrofit’s circumstances to your advantage, and this underground approach can rise above client expectations in short order.
A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.