An air handling unit that hasn’t worked since, well, ever. Chillers that have to work more often as a result — and an extra chiller just to attack the affected zone. These were the obvious symptoms, but what was the cause?
This is the second in a series of columns in which I am demonstrating examples of systems performance information that can be gleaned from trend log analysis. In these columns, I introduce a system or sub-system, show a trend graph, and then leave it up to the reader to discover the operational “issue” illustrated in the graph. The answer will be given at the start of the subsequent month’s column.
From a missing pipe hanger three floors down to steam traps past their prime, these stories show how steam system problems can originate inside the boiler room or far beyond it. Read more in February issue.