Read about various examples — from a 40,000-sq-ft raised-floor environment to a 5,000-sq-ft facility within a facility — to get a good view of the battlefield and make your next campaign against heat and inefficiency a little smarter.
The range of HVAC design options associated with the various types of data centers has expanded and evolved over the past 30 years in order to keep pace with the wide array of server transformations and deployment strategies.
October 29 was a Monday. It was also the day that Hurricane Sandy made landfall in New York City. Around 7 p.m., Con Edison shut power off in Lower Manhattan, and it would be sometime Saturday before lights would begin to flicker back on.
The author’s longtime interest in bundling efficiency techniques in a single system eventually led him to a new pairing: VRF zoning technology and geothermal design. See how he got there and how this couple played out for an historic 107-year-old Iowa courthouse that serves the law through the area’s brutal winters and humid summers.
Once again, we bring you an advance peek of what will be on the floor when AHR Expo attendees arrive in Dallas late this month. Attendees and non-attendees alike can also browse a treasure trove of info at www.ahrexpo.com. But for now, enjoy a snapshot drawn straight from the exhibitors themselves.
A few circumstances in a data center make it ripe for a CHP design to boost efficiency. Let’s get into the options within both relevant chiller types, why payback may be shorter than expected, and the assorted potential benefits from lower costs to higher reliability. Some tips from an array of manufacturers’ reps round out this useful investigation.