One of the worst things you can do is note the capacity and replace the chiller. Have the building loads and usage changed? What about motors and cooling towers? Consider these and your part-load realities to create real long-term improvements.
Retrieving every last bit of performance from the system while stopping short of the surge line is no small feat. Dig into sizing, tower selection, chilled water loads and stability, and condenser water management to leave no efficiency stone unturned. Read more in April issue